Question about KDS Valiant 6380iPTD-01 Notebook
Vaillant atmoMAG mini PT 11.Is possible a gas problem?
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
two pipes coming into boiler on right hand side have brass block valves with a small round recess. These two valves are linked with a stainless fill hose.
Inside the recess on each valve is a small slot, there is a "key" with the boiler but prob lost with the manual. The advantage of the key is its sized so you wont be poking it in the wrong place!
Using a screwdriver turn both slots throug 90 degrees, you will hear water running through. Sometimes one valve is left open so try a combination until the watert runs.
Keep an eye on the pressure gauge and dont let it get too high, if you have no idea of setting pressure head for about 1bar.
Posted on Nov 23, 2008
The answer is that your system is out of water pressure.
Usually there is a nob on the right under the base of the unit near to the small dial to the right of the front cover.
To enable the system to work correctly the needle on this dial should be in the Grey, about midway position.
Currently with fault F22 this will be lower to below the Grey and on the needle.
To bring the pressure back to the correct position, you need to turn this nob until you hear the water entering the system, KEEP AN EYE ON THE DIAL AND TURN THE WATER OFF AGAIN WITH THIS NOB ONCE THE DIAL IS IN THE CORRECT GREY POSITION AS MENTIONED ABOVE. DO NOT OVER FILL THE SYSTEM. I suggest you check this every six months or so.
Once this is corrected your unit will light up again.
Best of luck. Mike. N.
Posted on May 22, 2009
SOURCE: vaillant eco tec pro 28
IF the weather is extremely cold, and you're getting F28, the external pipework may be blocked with ice. Warm up the external pipes (lag them if you can) - and now see if your boiler will re-ignite.
A friend fixed our condenser boiler with this tip - hope it helps you.
Posted on Jan 09, 2010
Tips for a great answer:
Sep 30, 2015 | Office Equipment & Supplies
Sep 29, 2014 | Amana GMH950453BX Gas Furnace
Dec 13, 2010 | Heating & Cooling
Oct 15, 2010 | Heating & Cooling
Aug 02, 2010 | Heating & Cooling
Oct 19, 2009 | KDS Valiant 6380iPTD-01 Notebook
Jul 16, 2009 | Water Heaters
Jun 27, 2009 | KDS Valiant 6380iPTD-01 Notebook
Nov 04, 2007 | KDS Valiant 6380iPTD-01 Notebook
157 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: