Question about Garden
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Gas apliances have safety features built into them so you don't blow yourself up. The pilot heats a thermocoupler which tells the gas valve there is a flame, open the main gas to the burner. If you can see the flame area of the pilot look for a round post about 3/16 inch in diamiter. This should be directly in the flame, if not bend the bracket so it is in one side of the pilot flame. The thermocouple is attached to a mounting bracket. This will be held in place by a 1/4 inch hex screw. remove the screw and the capilary tube leading to the gas control valve. Before you do anything, close the main gas supply to the fireplace and disconnect the power to the fan. You may need to semi dismantle the fireplace to get the thermocouple. The gas valve end is a brass 1/4 pipe thread plug. Turn the outer nut and remove without twisting the tube. Reverse this order to install a new one. Besure not to twist the capilary tube, tighten brass nut 1/4 turn past hand tight. Your better heating supply house will have these in stock. Restarting the pilot will take a few tries because the gas was off. Your gas suplier would charge about $75 to fix this. if you don't have the proper tools and it dosen't look pretty stright forward don't do it. You could get dead.
Posted on Dec 02, 2008
Sometimes when you turn a gas heater off for some time, if the source tank has been turned off, the line will bleed the propane and the line will contain mostly air. This is especially true if the supply line is long. In order to light the pilot, you will have to hold the pilot lighting button down for a while (a full minute or longer, depending on the size and length of the supply line) before pure propane arrives at the pilot light jet. You should keep a lighted lighter at the jet so that when the gas arrives, the lighter will light it. After the pilot lights, you will have to keep the button pressed long enough for the thermocouple to get hot enough to set the pilot to stay on. When it is hot enough, you should be able to release the pressed lighting button and the pilot should stay on. If it does, you should be able to light the heater. If the pilot jet never lights, gas is not getting to the regulator. If the pilot will not stay lit after a period of time waiting for it to heat the thermocouple, the thermocouple or the regulator may be bad and need replacement. :-)
Posted on Jan 03, 2010
Check for how clean the bottom of the unit is. I know it seems small but when dealing with these amounts of electric current they are just that "small" and the dust can be shorting out the unit and not allowing the gas valve to release the gas. Its a safety thing, they dont want gas around an electrical short "go figure" lol
Posted on Jan 05, 2010
These guys are a division of Monessen, a gas fireplace manufacturer, and have a variety of millivolt switches, remotes and thermostats.
Posted on Jan 17, 2010
needs blowing out remove pilot tube from pilot remove injector and clean it out then replace it all test joint with soapy water to check for leaks
Posted on Jan 21, 2010
Testimonial: "Thank you. I'll try that...hopefully the pilot tube and injector are easy to locate so I can remove and clean out."
Tips for a great answer:
Jan 06, 2017 | Majestic Heating & Cooling
Dec 07, 2015 | Heating & Cooling
Feb 02, 2014 | White Mountain Hearth Empire Tahoe 36...
Jan 21, 2013 | Napoleon 36" Zero Clearance Top/Rear Vent...
Dec 07, 2009 | Heating & Cooling
Dec 01, 2008 | Heating & Cooling
100 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: