Question about Water Heaters
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: WATER IS NOT HOT
Check the thermastat, located in removable panel. warning dont set above 120- 130. If not the case it could be a bad heating coil. Easy to change in electric just googl a how to sitr. If your not Real Handy with Your Handa I would recomend calling a plumber to check heating element, Could be cheaper to replace
Posted on Jan 04, 2009
SOURCE: takes too long for hot water.
You need a recirculating line. You will have to hire a plumber to run a water line from the farthest fixture or to the fixture you are concerned about on the hot side and return it back to the water heater. this will cause hot water to constantly run throught the hot water line (via the recirculating line) and when you want to draw water from the fixture, you will already have hot water right at the line.
I know this works with standard tank water heaters, but it is a lil trickier with rinnai units(but very possible) if your plumber pleads the 5th and tries to sell you another unit call the Rinnai manufacturerand ask them how.
Posted on Jun 20, 2009
make sure it is wired correctly, check circuit breaker, check breaker built on to element. If all fails, and it is determined your not getting power to it, you may need a electrician. Be careful. good luck.
Posted on Oct 11, 2009
You have clog in the water line.
Since all hot water pipes are involved, clog is probably near water heater.
Buy pressure gauge at hardware store that threads onto hose connection.
Brady BTG 100 at Amazon
Picture of gauge
Check outdoor pressure for baseline pressure in your home.
Turn off electricity to hot water heater for an hour or two so there is not scalding water.
Open drain valve on water heater to see if water heater is clogged with sediment.
Put pressure gauge on drain valve and compare with outside pressure.
Open hot water spigot on bathtub and see if tank pressure drops ... if tank pressure drops significantly with bathtub spigot on, then clog is on incoming cold water before tank, and could be on outgoing hot water pipes too.
If tank pressure stays about the same, then clog is on outgoing hot water pipes.
Clog can be sediment caught in cold water shut off valve located above tank. Open and close valve and test pressure again. Take apart incoming cold water pipes above tank and check for sediment. Replace valve. Look at condition of cold water nipple on top of tank.
Sediment caught at hot water elbow near tank.
Sediment can fill up old pipes. Take apart hot water pipes above water heater and see condition.
Look at condition of hot water nipple on top of tank.
You may have to take apart pipes up to first or second elbow.
Pipes can decay at joint where copper pipe connects to galvanized pipe. Check for copper to galvanized connections on cold or hot pipes and replace section of galvanized pipe. Copper pipe will probably be good, the galvanized pipe will deteriorate. Replace copper-to-galvanized joint with 3/4" non-conducting union from hardware store
Posted on Dec 06, 2010
Tips for a great answer:
Dec 26, 2015 | Water Water Heaters
Nov 04, 2015 | Water Water Heaters
Mar 05, 2015 | Rheem 82v52-2 Tall Electric Water Heater...
Mar 26, 2013 | Rheem ELD80 Commercial Electric Water...
Oct 29, 2012 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Apr 28, 2012 | RELIANCE ELECTRIC WATER HEATER
Feb 01, 2011 | RELIANCE ELECTRIC WATER HEATER
Sep 26, 2010 | RELIANCE ELECTRIC WATER HEATER
Nov 22, 2009 | Water Heaters
Jun 29, 2009 | RTO Atwood Water Heater - 6 Gal LP
19 people viewed this question
Usually answered in minutes!