Question about Honeywell Whole House Humidifier TrueEASE HE300 Power unit
When unit is shut down, water keeps flowing through unit
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: HE440A Steam Power Humidifier
The most common cause of overflow is when hard water deposits build up and prevent the float from closing. You'll have to open up the unit, make sure there's no water in it, and clean out any mineral deposits.
The problem with these steam producing units is that there is no built in way to remove those deposits automatically. The water comes in, evaporates, and leaves anything else that was suspended in it behind.
Posted on Nov 14, 2007
SOURCE: Water flow through humidifier
The solenoid that turns on the water to the unit should not change the water flow, so you should get the same amount of water that flows into the solenoid. If you want less water, you can partially close the valve at the water source.
Posted on Jan 22, 2008
SOURCE: No Water flow thru Humidifier
Loosen the brass fitting where it connects to the soleniod valve. If water comes out your saddle valve is ok. Carefully retighten this fitting. With the humidifier turned on loosen the first fitting down stream from the valve see if water comes out. if it does turn the humidifier off and see if it stops, it should. That will tell you the the valve is ok then, just clean the filter and the oriface. if it does not turn on and off check the wiring. if ok replace the valve.
Posted on Mar 29, 2009
No, it will not stop flowwing if it is the water supply. A solenoid valve opens the flow everytime there is a call for humidity, but it stops at the humidifier when there is no call, so it will leak from that point until it is fixed or tightened.
Posted on Aug 20, 2009
Tips for a great answer:
Dec 30, 2011 | Aprilaire 550 Humidifier
Nov 14, 2007 | Honeywell HE440A1005 Humidifier
Dec 20, 2009 | Aprilaire 550 Humidifier
Aug 19, 2009 | Aprilaire Humidifiers
Aug 10, 2009 | Aprilaire 550 Humidifier
Feb 01, 2009 | Honeywell HE360A1027 Whole House...
Dec 16, 2008 | Aprilaire 600 Humidifier
Nov 30, 2007 | Honeywell HE360A1027 Whole House...
Apr 03, 2014 | Honeywell Whole House Humidifier TrueEASE...
52 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: