Question about Carrier Furnace Control Board Bryant HK42FZ034
My Carrier furnace has stopped working all together. I noticed that the red light on the control panel is blinking in a particular pattern - 2 short blinks followed by 4 longer ones. I tried to research what the different codes mean for this control panel but cannot find anything. Thanks in advance for any help@
Located on the schematic on the inside of the furnace door should be a key for the blink sequence. 2 short blinks then 4 long ones would be a code 24 on that data plate
Posted on Apr 14, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Furnace wont run
First of all when you flip the switch, it goes thru a startup sequence. THEN it turns on the Igniter (notice the red glow). Then the gas turns on.
Now at this point check the idiot light and it should be giving you a code of 34. That 34 (3 shorts 4 longs) says that there was a problem igniting the furnace. After it cycles thru at least 4 times and fails to ignite all the blowers, then is when you get a code 14 (1 short 3 longs)
NOTICE what's happening with ALL the burner Tubes each time it attempts to ignite. If only one or two are running....then this is your problem.
To fix all you do is take out the burner Tubes, look for debris, blow them out (blow from the front where all the jets are), and replace them in sequence from left to right (the tabs overlap).
Posted on Feb 01, 2009
Tips for a great answer:
Feb 20, 2015 | Home Security
Jan 24, 2008 | Goodman GMS90703BXA Heater
Mar 07, 2014 | Heating & Cooling
Apr 27, 2010 | Coleman Propane Forced Air Heater...
Jan 17, 2010 | Heating & Cooling
Nov 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 16, 2009 | Heating & Cooling
Jan 23, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 15, 2009 | Heating & Cooling
The Carrier Infinity has a control board that will flash out a pattern giving you a hint of what could be wrong. To find it, remove the cover off of the furnace and you will see a small round clear window. Look and count the blinks. Then compare that number to the diagnostic chart found on the back of the furnace access cover.
Let us know what the pattern is and we can help you more.
Oct 22, 2007 | Carrier 38CKC036 Air Conditioner
380 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: