Question about Goodman Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Hi, Could be a run capacitor on the fan motor. They usually swell up and or leak when they go bad. If not, the only real way to test them it with a specific capacitor tester. A new capacitor would be cheaper. Make sure that the outside unit is disconnected from power before opening it up, try to spin the fan blade by hand. If it doesn't spin freely it may need oiled if possible. See above solution. Your problem is the fan motor though so if this don't do it, It will have to be replaced. If this helps, Please rate my solution. Thanks, kstfas
Posted on Aug 31, 2007
If you are sure of the power then ya have a control problem thermostat set correctly? could be open low pressure switch I would call for service. Tom
Posted on Jul 03, 2009
Tips for a great answer:
Oct 06, 2013 | Goodman Manufacturing Goodman DSZC160601...
Sep 09, 2011 | Goodman CKL36AR36 Air Conditioner
Jul 30, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 21, 2009 | Goodman CLJ30AR32 Air Conditioner
Jun 16, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 10, 2009 | Goodman CKL30AR30 Air Conditioner
84 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: