Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a Certikin Genie
You could try resetting this as it could be caused by several factors (blown heat exchanger being one as Karl mentioned).
Hve you tried resetting from in Service Mode ?
To get to Servce mode you need to go ino User Setup Mode first (turn off the boiler via the panel switch - then hold the Lock/Reset button whilst turning back on). Once in User Setup Mode if you rotate the thermostats all the way clockwise (it should display the software version) Then press and hold the Lock/Reset button for 3 seconds.
This should put you into service mode and it is now possible to change/reset some of the control parameters.
If you try resetting the error.
This issue may be caused if the Flue or water stat is tripped (in which case reset the stat). If th Fan resistor remains open in the circuit then you will need tsomeone out to investigate as that may cause the GAS error too.
COuldalso be the Valve coils are faulty in wich case they need replacing (agians I would get an engineer outto confirm and do that).
I'm suyou probably tried all this but just in case...
If the roblem is solved can you advise what fixed it ?
Posted on Jul 01, 2013
Tips for a great answer:
May 19, 2015 | Pool & Spa
on Nov 08, 2016 | Zodiac Lm3-40 Salt Water Chlorinator...
on Nov 08, 2016 | Pool & Spa
Feb 09, 2014 | Raypak Pool & Spa
Dec 07, 2013 | Lochinvar ENERGYRITE 400K BTU PROPANE GAS...
Dec 07, 2013 | Lochinvar Energyrite Residential Heaters...
May 13, 2013 | Jandy Lx Pool & Spa Heater - Electronic...
Jul 06, 2009 | Teledyne Laars HEAT EXCHANGER ASSEMBLY,...
Jul 13, 2008 | Heating & Cooling
178 people viewed this question
Usually answered in minutes!