Question about Carrier 38CKC036 Air Conditioner
I can hear that the unit is trying to start but the fan is not turning and the unit is making a humming noise and seem like it is putting off heat
Replace the run capacitor. It is a silver cylindrical object located in the electical compartment of you outside unit. There is most likely three places on the top where different color wires are attached. One is marked F,or Fan. The center should be marked C, or Common, and the last should be marked Herm, with wiring to the compressor. Make sure you write down or label each wire you remove and it's correct location. They must be installed on the new part just like they were on the defective part. For you to know which dual run capacitor you need, the old one will have printed on the side either 370, or 440 v,as in volts. You must also need to know the microfarad rating and it is also printed on the side with the voltage rating. Since this is most likely a dual(runs fan and compressor) you should see two ratings abbreviated as mfd. Something like a 5mfd for the fan motor and perhaps a 35 mfd for the compressor. CAUTION !!! This device has line voltage and you must insure the power is off at the disconnect/ breaker BEFORE you begin the repair. Sounds complicated but really only takes a few minutes. The main thing is getting the right mfd and voltage ratings for the new part and keeping a record of where the wires were mounted on the old one, and putting them back the same place on the new part.
Posted on Jun 18, 2009
You have a bad fan motor of fan capacitor. Call service tech. Capacitor cost + service about 130. Fan motror depending about 250.00 Rus
Posted on Jun 18, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: heat pump not running
check your house circuit breakers first that should be labeled heatpump or outdoor unit
make sure it is on and or not tripped
then if you have a box outside near the outdoor unit open it up and see if there is a breaker or maybe fuses that could be blown
Posted on May 26, 2009
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Apr 22, 2014 | Frigidaire FAM157S1A Air Conditioner
May 31, 2011 | Heating & Cooling
Jul 07, 2010 | Heating & Cooling
Jan 19, 2010 | Samsung AW0603B Air Conditioner
Aug 07, 2009 | Fedders A6P09S2A Air Conditioner
Jun 22, 2009 | Weather King 10AJA3601AH Air Conditioner
May 26, 2009 | Goodman CPLE24-1 Air Conditioner
Jun 09, 2008 | Heating & Cooling
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
836 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: