Question about Amana Heating & Cooling
3 amp fuse on the thermostat control board keeps blowing. Have checked wires to thermostat .didnt find a short.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Air Conditioner malfunction
Hi, Sounds like you have a short in the control circuit to me. Turn off all power going to the unit. Write down or otherwise mark the wires leaving the control board going to the thermostat. Remove them from the control board. Replace the fuse. Turn power back on and see if the fan still runs. If it does, check and or replace the heat limit switch that brings the fan on during the heat cycle. It may just need adjusted. If the fuse blows, I would think that the control board is probably bad. If it doesn't blow, Remove the thermostat. Leaving all thermostat wires open check them with an Ohm meter. There should be no continuity between them. Twist all the wires together at one end and ohm them again at the other end. You should have complete continuity on all wires. If the wiring checks out, down power the unit. Double check your wire colors and rewire the control board. With all wires open at the thermostat, turn the power back on. Touch the RED wire to the YELLOW wire. The Condensing unit should come on. Touch the RED wire to the GREEN wire. The fan should come on. Touch the RED wire to the WHITE wire. The heat should come on. Down power the unit. Replace the thermostat. Test unit. If the fuse has lasted ok but blows now it is either wired wrong at the Thermostat or the thermostat is bad. I hope I have helped. NOTE: If you can not understand these instructions. Call a licensed Heating / Air conditioning company. kstfas
Posted on Sep 23, 2007
SOURCE: analog thermo.stat control kit
Have you tried removing the RH wire connected to the thermostat and try it ? This might rule out furnace as short in system. If it does the same, put RH- (heat) back on and try removing RC-(cool) , if it doesn't pop the fuse, you may have isolated the problem.?
Posted on Aug 23, 2008
Hi!!! Does your ac unit work fine?If not check your low voltage problem..You have a low voltage problem check the wire going out to your condensor make sure that they are not touching..Good luck..Check low voltage wires..short in progress..
Posted on Jan 04, 2009
The three amp fuse is installed in the board to protect from shorts or overloads created by disconnecting or reconnecting components when DC power is still connected to the system. If the fuse is blowing, then you more than likely have a short in the 12VDC system between the control unit and the thermostat.
1. Pull the cover off of thermostat and remove the +12 (or +7.5 depending on the model) wire. Access the other end of the wire in the AC compartment. Using an ohmmeter, touch the end of the wire at the AC with one lead and touch the control box with the other (or any ground source). If you get a reading other than OL or Infinity, then that wire is shorted out in the wall somewhere. If not, repeat the steps for the rest of wires except the ground of course. If all of these wires appear to be fine, you may need to take it in for some more extensive troubleshooting.
Hope this helps,
Please rate me!!
Posted on Jul 04, 2009
Tips for a great answer:
Aug 30, 2014 | Coleman Mobile Modular Home Gas Furnace...
Jan 10, 2014 | Rheem 14AJM49A01-RHSLHM4821 4 Ton 14.50...
Jan 22, 2013 | Amana GMH950453BX Gas Furnace
Nov 27, 2012 | Heating & Cooling
Feb 28, 2012 | Heating & Cooling
Jul 16, 2011 | Goodman CKL36AR36 Air Conditioner
Jul 16, 2010 | Goodman GMS90703BXA Heater
Apr 13, 2010 | Heating & Cooling
Jul 04, 2009 | Dometic 57915531 Air Conditioner
Jun 29, 2009 | Dometic Rooftop RV Air Conditioner
47 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: