Question about Hayward H Series Pool & Spa Heater 400k Btu Propane Gas Milivolt Ignition H400p1
I will start my pool filter and the heater will not turn on.
Does the heater sound like it is trying to fire? (Fan on, clicking sound). Check your filter pressure. If it is high, it may be causing the heater not to fire because the heater doesn't know the pump is running.
Posted on Apr 13, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Hayward H400 heater problem
LO usually indicates low water pressure. Check the pressure in your filter. You may need to backwash. If the filter is to clogged then the water pressure in the heater is so low that it won't activate the pressure switch. While checking the pressure turn the pump off and then on to make sure the pressure gauge is actually working. Also check the pressure coming out of the inlets into the pool. You should be able to tell if you have sufficient water pressure.
Posted on Jan 28, 2009
if means ignition failure check that gas is on, check for fauilty igniter wiring or connections, inspect gas valve wiring measure voltage across gas valve during trial to ignition if 24 volt replace gas valve if no 24 volt replace control module
Posted on May 19, 2009
Actually, the clicking is likely causing the shaking. Inside the manifold of a H100 is a stainless steel diverter plate that send some of the passing water into the heat exchanger and lets the rest past and back to the pool. When it breaks, you will hear a 'clicking' noise at it rattles in the water path. When it breaks, the flow to the heat exchanger is intermittent and you will begin to boil the water, causing the shaking. This situation is dangerous, especially without a pressure relief in the heater or pipe. As long as your water chemistry is sound, Hayward will usually cover this under warranty even if the unit is over a year old. Contact them to get a factory authorized repair rep out at: http://www.haywardnet.com/locator/
Posted on Jun 12, 2009
BO means that you have bypassed operations. ie automation. if no automation is present then press and hold the Down arrow and Mode button for 3 seconds.
Posted on Aug 23, 2009
CE= Communication Error between Control Module
and Display Interface Assembly
1. Disconnect and then reconnect power to heater.
2. Check for faulty wiring or connection.
Inspect Display Interface Wiring. Ensure Display Interface Plug is securely attached to Control Module. .
3. Control Module and/or Display Interface Assembly
are defective.Replace Control Module and/or Display Interface Assembly.
Here is a linkt oH aywardmanuals:
Posted on Jul 05, 2010
Tips for a great answer:
Nov 16, 2011 | Hayward H-series Electronic Gas Pool...
Aug 30, 2011 | Hayward H-series Electronic Gas Pool...
Jun 25, 2011 | Hayward H-series Electronic Gas Pool...
Apr 25, 2010 | Pool & Spa
Jul 07, 2009 | Hayward H-series Electronic Gas Pool...
Jun 06, 2009 | Hayward H-series Electronic Gas Pool...
May 25, 2009 | Hayward H - Series 400 Heater Top for In -...
Jun 30, 2016 | Hayward H Series Pool & Spa Heater 400k...
121 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: