Question about Freezers
I have a victory 2 door freezer. r-404a freon, cap tube system.
what is normal pressures
Normal operating pressures will change as the freezer reaches the selected temperatures on the inside. Normals of minus 14 degrees on the inside would be around minus 4 psi on the suction and 150 pis on discharge. Now checking the pressure will require a set of guages that have been purged with the same freon before connecting with the suction line on freezer. If not purged the suction line will draw outside air into the system and cause freezing of air and moisture inside the capillary tube rendering the freezer inoperative, Hope this helps, Sea Breeze
Posted on Nov 02, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2018 | Freezers
May 18, 2017 | Continental Freezer Wide...
Oct 03, 2010 | True 49 cu. ft. / 1388 liter Commercial...
May 09, 2010 | Freezers
Oct 17, 2009 | McCall Freezer 7-7045FT
Aug 13, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jul 11, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jun 26, 2009 | Victory Freezers
Apr 07, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jan 07, 2009 | Victory Commercial Freezer VSF-3
Apr 22, 2018 | Freezers
1,707 people viewed this question
Usually answered in minutes!