Question about Freezers
I have a victory 2 door freezer. r-404a freon, cap tube system.
what is normal pressures
Normal operating pressures will change as the freezer reaches the selected temperatures on the inside. Normals of minus 14 degrees on the inside would be around minus 4 psi on the suction and 150 pis on discharge. Now checking the pressure will require a set of guages that have been purged with the same freon before connecting with the suction line on freezer. If not purged the suction line will draw outside air into the system and cause freezing of air and moisture inside the capillary tube rendering the freezer inoperative, Hope this helps, Sea Breeze
Posted on Nov 02, 2007
Tips for a great answer:
Oct 03, 2010 | True 49 cu. ft. / 1388 liter Commercial...
May 09, 2010 | Freezers
Mar 25, 2010 | Freezers
Oct 17, 2009 | McCall Freezer 7-7045FT
Aug 13, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jul 11, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jun 26, 2009 | Victory Freezers
Apr 07, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Jan 07, 2009 | Victory Commercial Freezer VSF-3
May 19, 2008 | Hussmann Freezer 12 Facing Straight Glass...
1,610 people viewed this question
Usually answered in minutes!