Question about Heating & Cooling
Recently replaced the contactor on the ouside 5 ton compressor unit - the a/c inside comes on and shuts off the blower when thermastat preset temperature has been reached - the ouside unit continues to run. My thought is that the contactor points are locked in the closed position. Any ideas? Should I again replace the contactor?
VAC FLA LRA RFS
240/277 40 240 50
480 40 200 50
600 40 160 50
The system is wrong, the blower must run continuously , and the compressor is the will stop if the temperature setting is reached. The outside fan is the same as the comp.
Posted on Jun 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 07, 2016 | Intertherm Heating & Cooling
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Sep 28, 2010 | Panasonic CS-A12C Air Conditioner
Jul 09, 2010 | Goodman CLJ30AR32 Air Conditioner
Jul 06, 2017 | Ruud UAKA060 Air Conditioner
Jun 11, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 05, 2009 | Carrier 38CKC036 Air Conditioner
Mar 12, 2009 | Heating & Cooling
Sep 27, 2008 | Coleman Heating & Cooling
143 people viewed this question
Usually answered in minutes!