Question about Sanyo Split System Air Conditioner
My sanyo split rotary airconditoning unit is icing on the high pressure side tube and doen't cool much .. I tried to recharged with freon 22 but it didnt really improved much .. current is low at 7A instead of 10.2 ., compreesor thermal overload trip after some time . please advise..
Ok, on these units, if by high side line you mean the small tube going from outside to inside, that tube is actually on the low side, the metering device is in the outdoor unit. If you shut the unit down, let everything thaw then restart and find that small tube is freezing up right at the outdoor unit right away, my guess is its low on charge. I see that you put some in, make sure it is the right knid of refrigerant. they do not hold alot. Where is your suction pressure running. If you put 2 to 3 pounds with no change, you may have overcharged but that is telling you that there is a restriction in the line inside the outdoor unit, probably the filter if it has one, or the metering device itself. Let me know what you find.
Posted on Jun 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 24, 2016 | Sanyo Split System Air Conditioner
Jul 27, 2014 | Sanyo Heating & Cooling
Jun 29, 2011 | Sanyo Split System Air Conditioner
Nov 24, 2009 | Sanyo 4.4 cu. ft Counter-High...
Aug 21, 2009 | Sanyo Split System Air Conditioner
May 23, 2009 | Sanyo Split System Air Conditioner
May 17, 2009 | Heating & Cooling
Jan 04, 2008 | Sanyo 24KS62R Cool Mini Split Air...
474 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: