Question about Mitsubishi MXZ-2B20NA MSZ-GE09NA MSZ-GE09NA Mr Slim 16 SEER Heat Pump
What does it mean when MSZ-GE09NA top light is blinking on and off? It works for about 2 minutes, then starts blinking. Have tried turning power off/waiting/ then power on the unit. Other inside unit works fine on same (heatpump) compressor.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The Mitsubishi units have to be reset by turning off the indoor units by switching the remote or thermostat to off. Then turn off the breaker to the outside unit(s). After 30 seconds,turn on the breaker and then you can turn on the remote for cool. If no lights come on on the inside units, most likely you have blown a fuse soldered on the main PC board. At this point, call your technician. A goos tech will be able to wire in an in-line fuse holder so if it should happen again, you can easily replace the fuse. If you do see a light or two come on at the indoor unit but the outdoor unit does not start after 3 or 4 minutes, sounds like you will need to call a technician. Most likely you have a blown fuse on the main PC board of the outside unit. It is not an easy one to replace. Good Luck!
Posted on Sep 04, 2007
In your out door unit you will have a dual capacitor. One side will be used to help start the outdoor fan and the other side is used to start the compressor. I have a fluke 187 volt ohm meter and can read uF. You probably have a bad capacitor. Its easy to change and by far the cheapest thing to do before calling a tech. It is out side where the electrical enters the outdoor unit. Be sure to kill all power to the outdoor unit and ground the capacitor before you remove and test. This has been the summer of capacitors here in SW Missouri. I have replaced several in the area.
Posted on Aug 15, 2009
SOURCE: mr. slim MSZ-GE15NA indoor unit
There is either a problem with the outdoor unit fan or compressor or there is a communication problem between the two....
Did you check the number of blinks and then check the book to see what it means??...
Mitsubishi Air Conditioner Troubleshooting and Repair
Posted on Dec 29, 2010
SOURCE: Hey, i have a MSZ-GA80VA
Is there some error code.? Without knowing error code, chances for yor your problem is:
If indoor working properly, there is communication problem between indoor and out door. Check for power in out door after 3 minutes of a/c switched on. If no power problem with your PCB. Replace it.
Posted on Jan 19, 2011
Tips for a great answer:
Aug 05, 2014 | Protron PLTV-37 37 in. LCD Television
Nov 11, 2011 | Heating & Cooling
Jul 15, 2011 | Mitsubishi WS-55511 55" Rear Projection...
Jun 11, 2011 | Buffalo Technology LinkStation Quad...
Feb 18, 2011 | Mitsubishi MSZ-A15NA Split System Air...
Jan 18, 2011 | Mitsubishi Heating & Cooling
Dec 26, 2010 | Mitsubishi Heating & Cooling
Dec 16, 2010 | Mitsubishi MSZ-A24NA Split System Air...
127 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: