Question about Carrier Heating & Cooling
Old unit split type
Most possible reason in this case is defective compressor(it overheats),or not enough freon in the system. Solution 1.change compressor;2.Recharge the system with freon.
Posted on Apr 02, 2014
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
Tips for a great answer:
Aug 01, 2014 | Maytag Refrigerators
Dec 26, 2012 | Hitachi EC119SA Twin-Stack Air Compressor...
Oct 30, 2017 | Heating & Cooling
Jun 04, 2011 | Heating & Cooling
Jan 27, 2011 | Mitsubishi Heating & Cooling
Jan 16, 2011 | Fujitsu 18C1 Air Conditioner
Dec 16, 2010 | Mitsubishi MSZ-A24NA Split System Air...
Sep 20, 2009 | Refrigerators
Apr 14, 2018 | Carrier Heating & Cooling
127 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: