Question about APC MGE GALAXY 4000 75KVA-3-PH OL UPS 208V (GLF75KF) UPS System
Static switch will not turn on
Make sure that Bypass Phase Rotation is A-B-C. Check that Bypass voltage is within a tolerance of 208 +/-5%. Frequency tolerance is 60hz +/- 1hz.
Any condition not met, and Bypass will not be available
Posted on Jun 04, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 06, 2015 | MGE Galaxy 3000 UPS System
Apr 01, 2014 | MGE Pulsar MX 4000 (68501) UPS System
Dec 16, 2012 | MGE Galaxy 3000 UPS System
Nov 13, 2012 | MGE UPS Galaxy 3000 UPS System
Sep 14, 2011 | MGE Galaxy 3000 UPS System
May 26, 2010 | MGE Galaxy 3000 UPS System
Jul 29, 2008 | MGE Galaxy 3000 UPS System
86 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: