I moved into an apartment which had a Samsung window unit in the bedroom. After a year, it has quit cooling (the fan still works well). I also noticed I don't hear the compressor kick on and off any longer. I asked at the manager's office and discovered that the unit was left by the previous tenants and doesn't belong to the apartment complex! I loved having this air conditioner. Is there something short of hiring a serviceman that I might try to see if I can (or my boyfriend can) repair it?
An expert who has achieved level 2 by getting 100 points
An expert that got 5 achievements.
An expert whose answer got voted for 20 times.
An expert who has answered 20 questions.
Re: Window unit no longer cooling
You could pull the front cover off and see if there is a loose wire in the control box (behind where the control knobs are). it could just be a bad thermostat. you will see a copper wire with a silverish end on it coming out of the t-stat, try holding it between your fingers for a few minutes to warm it up, turn the t-stat to coldest setting possible, turn unit on, and then see if the compressor will kick on. if neither of those things help you could try replacing the thermostat, probably not expensive from samsung if the unit isn't too old. if that doesn't help either then the compressor probably bit the dust. but if not its worth fixing! hope that helps.
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
This is not Refrigerator This is Air Conditioner
you wrong category
This is the specs for you unit:
4.0kw Portable Air Conditioner (14,000btu)
Including Flexible Window Kit
• Suitable for any bedroom or small living
• No Installation Required
• Timer On/Off
• Remote Control
• 3 Speed Fan + Dehumidifier
• 3 Year Replacement Warranty
• Cooling Capacity: 4.0 Kw (Cooling Only)
• High Air Flow 570m3
• Plug Type: 10A
• Control Type: Manual Buttons or Fully Remote Control
• R410A Gas
The last is the KEY. the unit don`t work with water works with GAS R410A
This is compressor type Portable Air Conditioner
Since you don't give a model number, I will have to assume that it is a window unit, if not this probably won't apply. When a unit freezes up - as in ice on the evaporator fins it is usually either a low freon condition or the fan is not moving air accross the unit.
With the supper high temps that we are experiencing, many units that are undersized for the area that it is trying to cool are having serious problems. One client called us out to respond to a similar problem, so we charged the unit to factory specs. A few days later she called and said that the unit wasn't cooling properly, so we went back out. Since it was a window unit that was in the bedroom, it was a small unit. She was leaving her bedroom door open with fans to draw the cold air out to the rest of the house, which the unit was not sized to do.
The problem with window units and any service tech will tell you it cost more to repair than you can buy at Walmart or home depot. Unless you know someone who can charge it for you. Window units are a sore subject. A 200 dollar window unit might cost 200 dollars to charge system. SORRy rusty
I would consider replacing the t'stat if it does not seem to cycle at the desired temps. Also, the outside air allows fresh air to be introduced into the conditioned space but it will also effect, to a degree, the units ability to cool the conditioned space. Once you get the unit running, try it with the baffle on and closed and see which one you like. Remember, the outside air has and add humidity and can make it seem hotter than it really is in the room.
I recommend that if you have animal and you want to have the unit on all day that is fine if you have an ac unit with a thermostat and it is big enough to handle. The unit that is in the window is ok if your home but it could cost alot if there is no thermostat because it will run and run and run. Then if it don't cool the house enough means its not the right size. The unit / compressor could overload and kick on and off and might not work when you get home and the house will be like a firecracker.
Best bet would be to replace it with a unit for the size needed for the apartment. It would be effecient.
if we can help further just let us know.
This question is really to broad to answer. There are several things that could cause it to stop running. I think I would turn everything off, let it cool down for several hours and try it again. When you kick it back on, take note of what is running and what's not running. Inside fan, outside fan, compressor. If the outside unit will not run at all it could be as simple as a grasshopper caught in the contacts. If you hear the compressor running outside but no outside fan, The fan motor probably needs replaced. Please make sure that all power to the unit is TURNED OFF before removing cover plates on outside unit and before trying to remove insects from contact points. Check all wiring inside outside unit while it is open. Also check capacitors for swelling or leaking. If you don't know how to turn all the power off or open the outside unit, you need to call a professional AC technician. Hope this helps.