Question about Heating & Cooling
Fujitsu inverter R410a
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Yes, if the filters are clean, the coils are clean, and it is still freezing up in cooling mode, then it is low on refridgerant.
Posted on Jan 14, 2009
SOURCE: Senville Mini Split Error Code
The E4 light on your system is saying there is a commiuntion problem between the inside unit and the outside heatpump unit.Make sure there are no loose wires and you wired it properly,The S wire is the commiuntion link wire make sure it is a solid run between both units.I had the same problem with my system and it was the s wire not making a good connection.
Posted on Apr 25, 2009
is fan spinning fast enough it has to have alot of velocity to cool condensor coils if you haft to push fan to get going its probably shot and get new motor the ac is a sealed system and hardly ever will leak freon!!!Best of Luck to You!!! :)
Posted on Jul 02, 2009
This unit is use in motels etc. Check the ouside coil ( conderser) from the inside (discharge fan ) for dirt. Most of these units are floor level . This can cause a unit to short cycle ( cold air is at the floor) .
Posted on Jul 18, 2009
Tips for a great answer:
Nov 04, 2017 | Fujitsu Heating & Cooling
Jul 12, 2015 | Panasonic Heating & Cooling
Apr 22, 2015 | Fujitsu Heating & Cooling
Jun 14, 2014 | Goodman Heating & Cooling
Oct 10, 2013 | Fujitsu Heating & Cooling
Jan 24, 2013 | Fujitsu 24C1 Air Conditioner
Jan 14, 2009 | Carrier 52PQ307 Wall/Window Air...
Jul 30, 2008 | Heating & Cooling
May 24, 2008 | Fujitsu Heating & Cooling
May 14, 2008 | Fujitsu 24C1 Air Conditioner
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: