Question about Water Heaters
I have a 13 year old 50 gal gas water heater in the attic (I'm in Texas). I drain the tank annually. Only during very hot summer days (100+ temp) the pilot goes off by itself. It does not goes off unless attic temperature is very high. I changed the thermocouple but the problem remains. The vent goes straight out to the roof and it has a vent draft installed on top of the tank. The vent pipe sticks out of the roof about 2 ft. I was told perhaps the vent cap out in the roof was too small. Is there a recommended vent cap size for a 3" or 4" vent? what else could be happening? Thank you!
It sounds more like the pilot is being blown out by drafting.If there is any open shielding at or below the pilot light line , it is very possible for it to blow out.Hold a tissue between your fingers and ck for drafts around the burner and pilot area. If it's the case, The drafting needs blocking.the exhaust will still exhaust because of the heat it generates and confined location in the combustion chamber. Good Luck.
Posted on Jun 18, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 22, 2017 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Sep 30, 2013 | Whirlpool Water Heaters
Aug 16, 2011 | Rheem 50 Gallon FVR NATGAS Water Heater...
Aug 09, 2011 | Reliance Natural Gas Water Heater Control
Jul 30, 2011 | General Electric Water Heaters
Jul 29, 2011 | Whirlpool Water Heaters
Jul 28, 2011 | American Standard 40 G Natural Gas Water...
Jul 04, 2011 | Rheem Water Heaters
Apr 14, 2009 | Rheem 40 Gallon FVR NATGAS Low WATER...
Feb 10, 2009 | Rheem 50 Gallon FVR NATGAS Water Heater...
136 people viewed this question
Usually answered in minutes!