Question about Water Heaters
Oops, when I connected the the supply line to faucet, water shoots out the hot open connection, how do I cap that off?
Just cap the open hot connection. When the valve is set to any intermediate position between hot and cold water will flow from the hot side to the cold side if there is any pressure difference. In your case the difference is your water pressure. You did nothing wrong you just did not finish the install.
Posted on May 03, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I found a way to get warm water in the shower, but I'm not sure it qualifies as a solution. After trying everything else I thought that maybe when I was feathering the faucet in the shower toward the cold side so I would get warm water that at a certain point it blocked the flow on the hot water side enough so that the sensor in the hot water heater sensed there was no demand in the line and it shut the water heater off. To test this, I went to the kitchen and turned the kitchen sink faucet all the way to the hot side and then turned it on so that I got a small flow of water. I waited for the water to get hot to be sure the hot water heater was working. Once it was hot, I left it running to keep demand in the line and then I went to the shower and turned the faucet on. When the water got hot I started feathering the control towards the cold side and soon I had warm water. So I think I'm right in that the sensor in the hot water heater was shutting the water heater off when the demand in the shower was lowered to a certain point when I was trying to adjust the water temp in the shower.
So now I can get warm water, but it means I have to leave the hot water running at another fixture in the house to create a false demand in the system so the hot water heater doesn't shut down. Is there a way to adjust the senor in the hot water heater so that it will stay on when I'm using the shower only, so I don't have to waste water by running another faucet when I want to take a shower?
Posted on Nov 29, 2008
they have it installed wrong it is pulling from the wrong side, it is supposed to pull ot water up to the fixture but then if it stays hot on the cold side they are backwards
Posted on May 29, 2009
It could be back flowing into the hot water heater tank which is not full because of the leak. Even though the valve is closed on the cold water entry side, there is probably no valve on the exit side. That is how it is returning to the tank.
Posted on Sep 19, 2009
Testimonial: "Thank you very much, Rick! "
Double check that washers inside fittings attached to back of tank, are not wedged or pinched in there restricting flow. Drain tank, relieve water pressure prior, obviously. The other thing is to check that the by-pass is allowing good flow in to tank when in normal operation mode. Have seen those only go half way inside valve, but lever is at wide open setting. If all that checks out, try removing the check valve on tank, and replace it with a 1/2" galvanized pipe nipple, ( or certified plastic/nylon fitting same size) and reconnect water line direct to that, without a check valve. That should do it if nothing else was wrong. Now you have a choice, either change it or leave it out if everything seems ok, but double check that hot water isn't siphoning back to another utility such as toilet if you leave it out and toilet is close. Feeling that cold line (inlet) when water is hot should tell you. I've seen the check valve in both locations, hot (at top of tank) and cold (at bottom of tank -inlet) Not 100% sure why, right from factory that way, but I say, put it on bottom fitting if required at all. Let me know how you make out.
Posted on Oct 21, 2010
Tips for a great answer:
Mar 23, 2014 | Water Heaters
Mar 23, 2014 | Water Heaters
Jan 19, 2011 | Rheem 50 Gallon FVR NATGAS Water Heater...
Jan 08, 2011 | General Electric GE SmartWater Household...
Nov 16, 2010 | Rheem Water Heater Pressure Relief Valve
Oct 29, 2010 | RTO Atwood DSI-RV Water Heater-6 Gallon
Oct 05, 2009 | Grundfos Comfort Series Replacement Valve
Sep 14, 2009 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Nov 28, 2008 | Water Heaters
36 people viewed this question
Usually answered in minutes!