Question about Fujitsu 24C1 Air Conditioner
R and rc @stat to r on furnace
w @stat to w on furnace
g @ stat to g on furnace
y @ stat to y on furnace
from furnace 2wires going to out side unit typical red & white wire. red goes to y @ furnace and white goes to the neutral of the trans former . BE SAFE turn off power.
r = Red wire Hot
w= White wire heating
g = Green Fan
y= yellow cooling
if their is a B or C @ the furnace terminal board that the neutral . Tom
Posted on Jun 17, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
The "thermostat" is actually on the control board of the indoor unit, and is operated through the hand-held remote control. The remote also controls the indoor fan speed through the same board. The outdoor fan is a 2-speed, and is also controlled by the board in the indoor unit. The closest you'll get to a wiring diagram is on the inside of the cover where the wiring connections are made on the outdoor unit.
I had a condenser (outdoor) fan go bad, and it wiped out the control board, the power supply board, contactor, even the remote control, and eventually the compressor.
Posted on Jun 16, 2009
Tips for a great answer:
Sep 08, 2014 | Goodman Manufacturing GSZ140361 Heat Pump,...
Jul 26, 2011 | Heating & Cooling
Jul 14, 2011 | Heating & Cooling
May 29, 2011 | Haier HWR08XC7 Air Conditioner
Apr 29, 2010 | Heating & Cooling
Jun 15, 2009 | Fujitsu 24C1 Air Conditioner
Oct 19, 2008 | 1988 Daihatsu Charade
Jul 20, 2008 | LG LWHD1800R Wall/Window Air Conditioner
326 people viewed this question
Usually answered in minutes!