Question about Home Security
How is it fixed to the wall
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
did you mark which terminals you removed the wires from on the old stat? If not you will need to look on the furnace and see what letters they are connected to .. then connect to the same on the thermostat.
Posted on Mar 08, 2008
it sounds like the problem may be in the boiler and not the controller itself. Do you kno which is are the two wores that are the r-w for the thermostat take and purt them together and see if the boiler stays on or shuts off like it does with the thermostat. If it does then replace the reciever. If it doesn't then you have another problem. Good Luck
Posted on Jan 07, 2009
SOURCE: Need help with wiring thermostat
first do you have a heat pump unit or standard a/c? standard a/c connections at the thermostat go like this red wire to rh-rc which is the 24v power and you don't have to remove the jumper.white goes to w which is the heating wire yellow goes to y which is the cooling wire green goes to g which is the fan wire and blue goes to c which is the common wire. so if your stat has rc- rh ywgc you should be set if the wires on the furnace correspond with the same alpha designation.orange may be used if u have a heat pump unit otherwise it may just be a spare you cap off and leave behind the subplate.
Posted on May 31, 2009
The proper way to do it would be to use a small piece of wire stripped at the ends. Then use a small amount fo solder on each end to connect RC to RH. Or use a small piece of solid(stiff) wire and strip the ends. The wrap the ends around the connector and crimp them to make contact. I would not use a paper clip. A paper clip is not designed to carry 24volt current and could melt.
Posted on Nov 02, 2009
Tips for a great answer:
May 11, 2014 | Hunter Fan Company 5/1/1 Programmable...
Apr 23, 2008 | Hunter Fan Company 5/1/1 Programmable...
Feb 13, 2010 | Honeywell Programmable Thermostat Heater
Jan 22, 2010 | Honeywell Programmable Thermostat Heater
Oct 24, 2009 | Honeywell Electronic Programmable...
Jun 22, 2009 | Honeywell Programmable Thermostat Heater
May 31, 2009 | Honeywell Heating & Cooling
Apr 03, 2009 | Hardware & Accessories
Feb 11, 2008 | Honeywell Programmable Thermostat Heater
Sep 20, 2017 | Home Security
21 people viewed this question
Usually answered in minutes!