Question about Pentair Minimax NT Heater
My heater will start and run for about 30 seconds and then shut down..if i wait about 10 minutes i can try to start it again, but i get the same results..when it does run for the 30 seconds or so, there is heat coming from the exhaust and the gas at my meter is running strong. thanks in advance..jeff
When a heater runs for 30 seconds or les some heaters run or about 1 minute this is mostly a problem with how much water is getting in the heater if is too little the pressure switch cuts the heater off or the high limit switch is shutting off the boiler why because the small amount of water getting inside your heater get hot to fast and make the heather to get so hot and the high limit switch turns the heater off the solution is to check your filter make sure is clean or cleaned they get dirty soon if your filter is clean and still doing it check the bypass in the heater normally is located next to the lines going in and out in the heather lines I have fix so many heaters my self I use to have a business in california as swimming pools repair so I know this and your heater is not to big to say is your gas regulator gs regulator is a common problem on heaters ranging on size from 30-36-40 BTU
Posted on Jun 15, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 29, 2016 | Heating & Cooling
Nov 18, 2012 | Cars & Trucks
Aug 12, 2011 | 1989 Ford F 350
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor.If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Dec 11, 2010 | Mr. Heater Natural Gas Garage Heater -...
Feb 17, 2010 | Reddy Heater-30-55,000 BTU Variable
Jan 10, 2010 | Dayton Gas Furnace Heater
Feb 08, 2009 | Kenmore 62602 Electric Dryer
492 people viewed this question
Usually answered in minutes!