Question about Whirlwind FH-778 Air Conditioner
Power was out for 3 days from storm; fan is now blowing, but no cooling. I've checked breaker inside and at condenser; thermostat appears to be working. what else should I check?
Ok if you have split system if indoor fan runs then transformer is working you have 2 breakers 1 for indoor and 1 for out door also disconnect at unit may have fuse in it if all seem ok remove side cover and look at capacitor if sweeled up bad take an insulated object and push in contactor if runs check for 24v from common to yellow stat wires also look for reset button next to freon lines hope this helps
Posted on Jun 14, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 29, 2015 | Heating & Cooling
Sep 25, 2015 | Heating & Cooling
Jun 07, 2017 | DeLonghi Heating & Cooling
Sep 29, 2012 | Ruud Heating & Cooling
Aug 28, 2011 | Heating & Cooling
Dec 16, 2017 | Coleman Mach 15 Air Conditioner
Aug 20, 2009 | Emerson Televison & Video
Jun 19, 2009 | Ruud UAKA042 Air Conditioner
May 30, 2009 | Heating & Cooling
175 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: