Question about Goodman CLQ36AR49 Air Conditioner
Check sub cooling and super heat. the New ac units are very critical to charge. There is a charging chart on the inside of the cover to the unit outside. Check temp difference across coil. Should be 18 to 22 degress. If you have an ampmeter. Check the heat strips one 5 kw might be stuck.(sequencer). This would cause you not be able to pull down temp. Goodman unit are hard to charge to get the temp difference across coil. Feedback please
Posted on Jun 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Jun 01, 2014 | Goodman CLQ36AR49 Air Conditioner
Feb 11, 2013 | Goodman GPH1524M41 2 Ton 15 SEER...
Apr 18, 2017 | Heating & Cooling
Jul 25, 2011 | Danby DPAC10031 Air Conditioner
Apr 08, 2017 | Goodman PHKJ048-1 Air Conditioner
Dec 26, 2010 | Heating & Cooling
Dec 15, 2010 | LG Heating & Cooling
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
553 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: