Question about Heating & Cooling
Sounds like the furnace is tripping off on a limit safety, either temperature or air switch. Check filters and restrictions to air flow (furniture over return air grills, blocked filters) also, check the drainage line of the system. If the furnace can't drain water fast enough it will back up internally, and trip the system off on a pressure switch safety.
hope this helps.
Posted on Apr 02, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Goodman heating system
It really depends on the type of system you have. You will either have a furnace, high efficiency furnace, heat pump system, heat pump with gas or electric back up heat. All these systems operate differently and the problem that you are having could be caused by multiple issues, depending on which system it is. More info will be greatly appreciated. Make sure to check all filters and air flow first before going any further. The system could be over heating and tripping a limit, causing the system to stop producing heat until the unit has cooled back down.
Posted on Dec 07, 2013
Tips for a great answer:
on Jan 19, 2010 | Heating & Cooling
Dec 06, 2013 | Heating & Cooling
Mar 02, 2011 | Amana Heating & Cooling
Jan 08, 2011 | Goodman Heating & Cooling
Nov 12, 2010 | Goodman GDS80904BNA Open Flame Heater
Feb 04, 2009 | Goodman GMS90703BXA Heater
Nov 30, 2008 | Goodman Heating & Cooling
Mar 18, 2008 | Heating & Cooling
103 people viewed this question
Usually answered in minutes!