Question about Hardware & Accessories
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
First check to see if you have afloat switch inside the air handler ar underneath the air handler. Its purpose is to shut the outside ac off if the drain stops up. Very common. If this is OK take cover off unit and with screw driver push in the contactor. It is located about the middle of the panel. It has main power at the bottom. If unit comes on you cave a control voltage problem. Meaning something is not allowing 24 volts to the contactor. If your out of Refrigerant the low pressure swich will have it off. Call a service tech. Rusty
Posted on Jun 09, 2009
The attic fan is not a part of your a/c system, and you should not run it while you are running the a/c. If you are currently using the attic fan, it is possible that someone wired it so that the a/c won't turn on while the attic fan is on. Otherwise if the thermostat is set below room temp, and says it is calling for cool, then the problem is most likely coming from an issue at the outside unit itself. Make sure to check your fuses, at the fuse panel and outside breaker. Hope this helps
FYI.. the only part of the system that might use batteries is the thermostat.
Posted on Jul 28, 2009
hi...first thing to do is canvas the price of the ceramic glass top,coz the price of the glass is half or more compare to the new one..do u think if u buy a glass only it is reasonable or waste ur money?then dont try to fix it by it ur self,coz the glass u buy is no warranty for wrong instalation.call an expert technician to do it to get an assurance for the warranty for installation.
Posted on Sep 13, 2009
Tips for a great answer:
Jan 05, 2018 | Cars & Trucks
Sep 01, 2014 | Heating & Cooling
Aug 09, 2014 | Broan nutone Broan/nautilus Bathroom...
Aug 31, 2011 | Heating & Cooling
Jun 23, 2011 | Heating & Cooling
Jun 17, 2011 | Heating & Cooling
May 16, 2010 | Ruud UBHC Air Conditioner
Jul 28, 2009 | Heating & Cooling
Jun 09, 2009 | Heating & Cooling
Mar 10, 2009 | Heating & Cooling
59 people viewed this question
Usually answered in minutes!