Question about LG Art Cool LA121CNP wall/window Air Conditioner
Compessor start but fan dosent runs
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
Tips for a great answer:
Dec 22, 2017 | LG Heating & Cooling
Mar 30, 2016 | LG Heating & Cooling
Jul 14, 2012 | LG LD651EBL Dehumidifier
Jul 07, 2012 | LG LHD65EBL Dehumidifier
Apr 16, 2012 | LG Dehumidifiers
Aug 25, 2010 | LG Heating & Cooling
Jun 23, 2014 | LG Art Cool LA121CNP wall/window Air...
80 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: