Question about Kohler 30RESA 30kW Standby Generator Beige, Standby
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Your gas pressure is too low and you may not have a large enough supply pipe. You need at least 10 inches of water column with the engine running to operate an LP vapor fueled engine. Because the engine is starving for fuel, its governor opens the throttle to WOT (so it goes to high revs) but there isn't any fuel to make horsepower with so the output voltage falls and the undervoltage alarm trips.
Posted on Dec 03, 2008
SOURCE: kohler lp shuts down
What you need to know is there enough fuel going to the regulator. It should be 7 to 11 inches Water Column. If not your problem may be not enough fuel. That includes when the heater in your house kicks on and what ever gas appliance you may have. Once you verify that you need to figure out if you have the proper pressure coming out of the regular on the inside of the generator. Next I would look at compression of the cylinders. It may need new piston rings.
Posted on Oct 09, 2009
Tips for a great answer:
Nov 24, 2015 | Kohler 18RESL 18 Kw Generator
May 19, 2015 | Kohler 20resa 20kw Home Emergency Backup...
Dec 13, 2014 | Kohler Electrical Supplies
Sep 30, 2014 | Kohler Electrical Supplies
Jun 12, 2014 | Kohler Electrical Supplies
May 26, 2013 | Kohler Electrical Supplies
Aug 18, 2012 | Kohler Electrical Supplies
Mar 22, 2011 | Kohler Electrical Supplies
Sep 24, 2009 | Kohler Electrical Supplies
Dec 13, 2008 | Kohler 12 kW Emergency Power System -...
51 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: