Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
F6 error is related with the indoor blower motor check the return signal wire of motor with the small connector and fix it properly.
Posted on Jul 29, 2010
SOURCE: i'm getting error code F6
F-6 High discharge coil temp. due toover charged /condenser coil blockage/less rpm of fan motor in outdoor/non-condensate gas.
Purge out over charged gas/clean condenser coil/Replace fan capacitor./Releaseall gas and flush out the system,replace filter drier and vacuum & do gascharging.
Posted on Dec 31, 2010
Tips for a great answer:
Dec 24, 2016 | LG Heating & Cooling
Jun 05, 2016 | Heating & Cooling
May 23, 2016 | Electrolux Heating & Cooling
Feb 19, 2016 | Heating & Cooling
Apr 10, 2017 | Heating & Cooling
Mar 15, 2013 | LG LS-L1210CL Mini Split Air Conditioner
Mar 10, 2012 | Heating & Cooling
May 09, 2010 | Heating & Cooling
225 people viewed this question
Usually answered in minutes!