Question about Cadet Manufacturing 67507 Heater
I have two cadet wall mounts ea. 1500/240. The thermostat has two romex w/ one being 240- I connected ea. of the white leads together and then connected the remaining blk leads to a single pole therm. The issue is it keeps triping the duel 20/20 breaker and to add- when I connect the two white leads I have 120 at ea. heater but when I connect the remaing blk leads to therm. the breaker will trip-any suggestions? Thanks John at firstname.lastname@example.org
Your wiring is all wrong. for a 240 heater a 20/20 tandem breaker will not work with a 240 heater. you need a 20 amp two pole breaker. the two wires at the heater need to be connected to the line. you probably have two black wires at the heater. one connects to the white romex which should be taped black, and the other romex black connects to the other black wire. at the panel one white goes to one side of the breaker and the black to the other. the bare ground goes to the neutral bar.
Posted on Nov 05, 2007
Tips for a great answer:
Dec 12, 2013 | Heaters
Dec 23, 2012 | Heaters
Feb 26, 2011 | Williams 3003622 Ceramic Wall Mounted...
Jan 11, 2011 | Cadet Manufacturing Register Plus RM202...
Jan 02, 2011 | Dimplex Heaters
Dec 26, 2010 | Williams 3003622 Ceramic Wall Mounted...
Feb 23, 2008 | Heaters
Nov 28, 2007 | Heaters
Nov 13, 2006 | Empire GWT-25 Wall Mounted Panel Heater
604 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: