Question about Heating & Cooling
My friend has a Bryant plus 90 furnace. it starts up fine, ignites, blower runs, but the air its blowing is not warm at all. they can only get their house up to about 62 degrees. it does not have any error codes. intake and exhaust pipes checked outside. no blockage. any suggestions?
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
PRSSURE, DRAFT SAFGUARD, AUX-LIMIT SWITCH(WHEN USED)OR BLOCKED VENT
SWITCH(WHEN USED) DID NOT CLOSE OR REOPENED (DOWNFLOWONLY)
If open longer than five minutes, inducer shuts off for 15 minutes
* proper vent sizing
* defective inducer motor
* restricted vent
* excessive wind
* low inducer voltage(115VAC)
* defective blower motor or capacitor
* defective pressure switch
* inadequate combusstion air supply
* disconnected or obstructed pressure tubing
If it opens after trial for ignition period, blower will come on for
90 sec. recycle delay.
Check your air filter for blockage, check pressure switch for a buildup of moisture. Make sure your inducer motor is turning and creating a vacuum to the pressure switch. Make sure all venting is clear and free of water or debris. Make sure there is no water in inducer motor and all drains are draining.
Posted on Jan 28, 2010
Tips for a great answer:
Feb 14, 2016 | Cars & Trucks
Jan 17, 2014 | Heating & Cooling
Dec 08, 2013 | Kitchen Appliances - Others
Oct 19, 2013 | Heating & Cooling
Sep 03, 2013 | Bryant 92 Afue Gas Furnace Legacy359aav...
Sep 25, 2012 | Bryant Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Nov 17, 2010 | Heating & Cooling
Feb 02, 2010 | LG LW1200ER Air Conditioner
Jan 28, 2010 | Heating & Cooling
322 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: