Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Rmove the two screws holding the blower in place and slide it out. With the power off, rotate the wheel and inspect for debris or an impingement. If everything turns easy, you have a bad motor or start capacitor. If you have rubbing, adjust the wheel. If the motor will not turn, replace it.
Posted on May 30, 2008
I have a goodman GMP075-3 that won't turn on. I think it is the pressure switch since I do not have a vent blockage. What is a venter and where can I find it??
Posted on Dec 30, 2008
Keep in mind all furnaces and circuit boards are not the same. Look on the back of the door to the blower compartment. You should find the list of diagnostic codes. Look up four blinks it should narrow down the problem. Although from the discription you gave it sounds lie the high limit control. When a high limit appears to be acting up it DOES NOT mean that the high limit needs replaced. The high limit just may be doing its job. This means that the furnace is overheating. Check your filters. Are all of your registers open? Is your blower set on the right speed? Is your blower going bad? Is the blower motor capacitor bad? Is your evaporator coil restricted? Just changing a high limit switch does not always solve the original problem!
Posted on Apr 03, 2009
The board is bad. The unit thinks a flame is present, so it tells the blower to come on. Replace the board.
Posted on Oct 08, 2009
sounds like the circuit running to your condenser powers your furnace. when u disconnect power to the furnace it will reset and run the blower on startup. check the tube connecting the vacuum switch to the induced draft motor. maybe a leak. good luck
Posted on Nov 24, 2009
Tips for a great answer:
Feb 12, 2015 | Coleman Heating & Cooling
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Sep 24, 2011 | Goodman CKL36AR36 Air Conditioner
Nov 05, 2010 | Goodman PHKJ048-1 Air Conditioner
Mar 22, 2017 | Goodman Heating & Cooling
Oct 23, 2010 | Goodman CKL24AR24 Air Conditioner
Jun 04, 2009 | Goodman CKL24AR24 Air Conditioner
May 23, 2009 | Weather King 10AJA3001AH Air Conditioner
39 people viewed this question
Usually answered in minutes!