Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: wont stay lit
go to this site www dot desatech dot com. Here you'll find parts to repair your heater. a propane heater uses a millivolt generator to sense the flame. along it's cappilary are two push on spde connectors. these connect to the high limit temperature sensor which is mounted on the flame backplate of your heater. to see if it is the high limit shutting down your heater, jumper across the two spade connectors. if the heater stays on, this is your problem. if the flame still goes out, then the millivolt generator is shot.
Posted on Nov 10, 2007
Hi , you can try and pull the panel on the bottom of fireplace out and check the adapter in fireplace. Sometimes they go bad. When you open in also check to see if there is an adapter plugged in and a option to use the battery operated function. If this goes bad the pilot will not stay lit.
Posted on Jan 14, 2009
You may need to replace the Thermocoupler. It screws into the gas regulator and the sensor end is set in the flame of the pilot light. You can get one at any appliance parts store. The Thermocoupler simply feels the heat of the pilot light and sends a very small amount of voltage to the gas switch that opens when your thermostat calls for heat. If the pilot light isnt lit, no voltage from the sensor and no gas can be released by the regulator.
Anyone can replace one. Just find the tip that sits in the the pilot flame when you try to ignite the pilot light. Follow it down to the regulator and unscrew it. There is no gas involved. It is Ultra Low Voltage. No danger.
Be sure to turn off the power to the unit before you begin removal. Take it to the parts store along with your furnace brand and model number. If you see any identifiers on the regulator, note them and take them with. When you replace it be sure to have the sensor end up in the flame of the pilot.
Posted on Sep 29, 2009
Make sure the pilot is clean (Blue flame fully enveloping the top portion of the thermocouple) if its dirty the pilot will be yellow like a candle and barely touching the thermocouple ...quick fix is knock the pilot with a screwdriver...gently tapping it...knocking the dust out and getting a better pilot....the pilot could also be too small if its not making good contact with the thrermocouple....there could also be an Auxillary limit wired into the thermocouple which when open will prevent the magnet from staying closed....if all looks fine then the Gas Valve itself is likely gone (The magnet inside is not field repairable)
Posted on Oct 25, 2009
Tips for a great answer:
Jan 10, 2016 | Robertshaw 720-007 universal gas valve for...
Jan 14, 2015 | Heating & Cooling
Jun 25, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Dec 18, 2012 | Napoleon 36" Zero Clearance Top/Rear Vent...
Nov 19, 2010 | Reddy Heater-30-55,000 BTU Variable
Feb 06, 2010 | Vulcan GR45 Deep Fryer
Nov 26, 2009 | Heating & Cooling
Jul 16, 2009 | Kenmore Dryers
Jul 12, 2009 | Bosch & Tankless LP Hot Water Heater
Jan 26, 2009 | Williams 2509612 Ceramic Mid-Size Heater
Aug 21, 2017 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!