Question about LG LSN121HSV2 11,200 BTU 20 SEER Ductless Heat Pump Air Conditioner Air Handler"
Cooling lights flashes 5 times no heat no nothing
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On a heat pump the difference from heat to cool is the reversing valve.
In cooling or heating the Y1 terminal will always be energized, this is the contactor.
Depending on brand the reversing valve will either be energized in Heat or Cool. At the outdoor unit check to see if the reversing valve is getting 24 volts in cool, if not check to see if it is getting 24 volts in heating. The easiest way to check if the reversing valve is shifting, is to feel the big copper tube, (it is not the suction line on a heat pump) this is a refrigerant vapor line. It will be cold in cooling and hot in heating.
Check your thermostat installation instructions and heat pump installation instructions to determine the proper terminal designations for your heat pump and thermostat. There are some brands out there that use the B terminal as common to the 24 volt circuit, so you have to check the wiring and make sure this is not common.
If it is energized in Cool then the Y1 and O terminal will be energized. You will have 24 volts from common usually the C terminal to Y1 and O.
If it’s energized in Heat then the Y1 and B terminal should be energized. You will have 24 volts from common usually the C terminal to Y1 and B.
If you get heat when you’re calling for cooling or vice versa then switch the wire between the B and O terminals.
Posted on Feb 10, 2010
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor. Thanks.
Posted on Feb 05, 2011
Tips for a great answer:
May 21, 2017 | Honeywell Heating & Cooling
Apr 22, 2017 | Fujitsu Heating & Cooling
Mar 07, 2016 | Heating & Cooling
Oct 25, 2013 | LG LSN091HSV / LSU091HSV 9,000 BTU 20 SEER...
Jan 18, 2013 | LG LSC121PMA Split System Air Conditioner
Sep 21, 2017 | Heating & Cooling
Jul 25, 2011 | Heating & Cooling
Nov 18, 2009 | LG DLE7177 Dryer
24 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: