Question about Mr. Heater Natural Gas Garage Heater - 45,000 BTU
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
turn off propan and heater. Undo the connector hose. then rehook hosewith heater valve off, Turn on propane valve real slow. Propane bottle valves have a safety that senses rapid escape, like in a wide open dump. This should reset it.Then light the pilot . should work.
Posted on Jun 10, 2009
Hi clean the flame senser blow the dust out of the heater check the fan switch might be dusty jump out pressure switch see if that helps
Posted on Feb 02, 2010
Is the circuit board giving you a blinking error code?
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Feb 26, 2010
Tips for a great answer:
Jan 11, 2016 | Mr. Heater Heating & Cooling
Feb 18, 2014 | Mr. Heater Natural Gas Garage Heater -...
Nov 02, 2011 | Mr. Heater MH12CS with Electronic Spark...
Jan 17, 2011 | Mr. Heater Portable Kerosene Heater -...
Feb 02, 2010 | Mr. Heater Natural Gas Garage Heater -...
Jan 04, 2010 | Reddy Heater-170,000 BTU Kerosene Deluxe
Oct 06, 2009 | Dryers
Jun 08, 2009 | Mr. Heater Propane Outdoor Heater/Cooker
Apr 11, 2008 | Scheu (K50-FA) Heater
Feb 03, 2008 | Heating & Cooling
Oct 18, 2015 | Mr. Heater Natural Gas Garage Heater -...
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: