Question about Amtrol ST-12-C THERM-X-TROL ASME Expansion Tank, 5 Gallon
Not getting enough hot water
The answer different if you have: concerns about diseases, a dishwasher, young children or elderly that can be easily burned, electric vs. gas heat, type of plumbing (e.g. PEX or Copper).
In 1988, the Consumer Product Safety Commission recommended that water heater manufacturers preset the maximum temperature at 120 degrees Fahrenheit to prevent burns. Since several states have mandated this maximum temperature.
Posted on May 03, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Since you mentioned 'both temperatures' it seems your unit is like most all of them, a lower and upper coil.
If your hot water supply runs out quickly, this normally means that the lower coil has failed. Since heat rises, the upper coil will never supply a tankful of hot water, just hot to start, and then as the flow continues, it doesn't have time to do more than warm the water flowing into the tank.
Every home should now own a simple digital multimeter; they cost less than $20 US everywhere and one can find them in auto parts stores, electronic supply companies and tool companies.
If you have a Harbor Freight tool store in your area, you can get them for under $10 US any time and sometimes even less:
You need to be absolutely certain that the voltage to the water heater is shut down. Before you measure anything else, set the meter to its highest AC setting and check across the coils and then from either contact to the metal housing. If it is dead everywhere, then set the meter to the lowest Ohms scale (normally 200). The resistance of the coil should be nearly the same reading as when you simply short the meter's probe tips together. If it measures 'OL' then the coil is open and must be replaced.
Posted on Feb 26, 2009
Tips for a great answer:
Nov 04, 2014 | Amtrol WHS-80Z - WHS-80Z 80Gal Hot Wtr...
Apr 08, 2014 | Water Heaters
Feb 19, 2013 | General Electric GE SmartWater Household...
Oct 27, 2012 | Rheem Tankless Water Heater Main Remote...
Aug 05, 2012 | Rheem Tankless Hot Water Heater...
May 17, 2010 | Rheem Tankless Hot Water Heater...
Jan 04, 2010 | RELIANCE ELECTRIC WATER HEATER
Feb 17, 2009 | Noritz 7.1 Gpm Natural Ng Gas Tankless Hot...
Aug 27, 2008 | Emerson Part UWL Chrome Ultrasystem water...
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: