Wiring- Connecting wiring on replaced fan motor
Your new fan motor should have a diagram with it or at least printed on the side of the motor, that will help a lot from your end. As for me, I don't know what unit you have, so I will try to help you with just the basics.
Your old motor probably had 3 wires. One went to the contactor, that is the "Line Voltage", one went to the Common terminal on the old capacitor (COM), that's the other "Line Voltage" wire, and the last one went to the "FAN" terminal on the old capacitor. The reason the old capacitor looks different is because it works for both the compressor and the fan motor (split capacitor). You still need this hooked up for the compressor to work.
The new fan motor.
These vary in brands and wiring so I can not tell you the colors without knowing exactly which motor you have. On the new motor wiring diagram, you should see the "Line Voltage" as described above that 2 of the wires are ran to each other (just on the diagram, not wired together on the unit). This is your power wire that goes to the contactor on the unit, usually black, and your Common wire that runs to the capacitor. You can still run this wire (COM) to the common terminal on the old capacitor since you still have to use the old capacitor for the compressor and the common terminal should still be jumper-ed from the contactor to the (COM) terminal. Then you will probably have 2 wires for the new capacitor, usually Brown and Brown/White. These wires run to each side of the new capacitor and doesn't matter which terminal. Then you will take a new jumper wire from the (COM) terminal on the old capacitor to the terminal on the new capacitor that has your Brown/White lead. Make sure you secure the capacitors inside the unit so not to touch anything surrounding them. Your new motor might also be a "Reversible" motor that has reversing wires also. Again, your new motor diagram can tell you how to hook these up. You have to have it spinning the right way, most of the time it is CCW (counter-clockwise).
I'm sorry I can't be any clearer on this, but without knowing the brands, models, etc, I'm in the dark. If you need any additional help, I would be glad to help! Good luck and hope you get to cooler days!
Jun 28, 2012 |
Heating & Cooling