Question about Heating & Cooling
Outdoor unit PC wiring and test signals
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
1.sensar of remote control.
2.indoor unit sirkit board may be there is problem.change sirkit board by new one
3.if any requirement abt airconditioner pls mail me i can send u spare parts of air conditioner,.
Posted on Mar 16, 2008
Electronic filters use static dicharges to filter the air. Unfortunately the make that clicking noise when they discharge. LG calls it a plasma filter. Clean both the regular and the plasma filter to see if that helps.
Posted on Dec 30, 2008
The outdoor unit should have 2 small wires connected to the contactor coil. This delivers the 24v "Signal" to energize the coil. The wire from the t'stat for cooling are usually yellow, in almost every case. When you put the t'stat in the cooling mode and set the temp lower than the room temp, the indoor and outdoor unit should come on. Check for voltage on the terminal block for 24 volts accross the yellow and common wire. Common could be ground on some handlers. If you have the 24 volts, then check for 24v on the 2 small wires (usually 18 to 22 gage wire) on the contactor coil. If no voltage, trace the 2 wires back to the indoor unit and see where they go. If they are the ones that are not attached, put one on the yellow wire terminal and the other on the common terminal. This will send power to the indoor unit and then piggyback to the outdoor unit. Do not remove the yellow and common from the terminal block. Don't be too concerned about the colors from the outdoor coil wires. Just make sure they are hooked up right. Good Luck and hope this gets it going.
Posted on Jun 07, 2009
Tips for a great answer:
Oct 26, 2013 | LG Heating & Cooling
Oct 25, 2011 | LG LA185HV Split System Air Conditioner
Oct 21, 2011 | Heating & Cooling
Jun 16, 2011 | Heating & Cooling
Aug 24, 2010 | LG Art Cool LA181CNW Split System Air...
Jul 20, 2010 | LG Art Cool LA1000PR Air Conditioner
Feb 12, 2010 | LG Heating & Cooling
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
Aug 21, 2017 | Heating & Cooling
25 people viewed this question
Usually answered in minutes!