Question about Mitsubishi Heating & Cooling
Indoor unit of Mitsubishi Air-con Ceiling Cassette w/ model No. FDT100VD is keep on blinking and automatically turn off. The suction charge is 125psi while the discharge is 120 psi. what does it mean since the unit is not functioning well.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
E39 Fault is thermister, Mitsubishi way of saying im not going to start because there is something wrong. Generlly it is compressor fault or short of gas. Im guessing if you turned the power out. Waited twenty seconds, turn it back on. Now if you go to the outdoor part. Wait exactly 3 mins. If you hear the compressor try to start and fail then it would more then likely be your compressor if you dont hear anything and the unit faults out it will either be a board or short of gas.
Either way If the unit is under five years old get a warrenty agent out to look at it.
Sorry I couldnt tell you for sure but MHI are very vague when it comes to fault codes
Posted on Mar 05, 2009
SOURCE: p8 eroor code
P8 error is abnormal pipe temperature indoor. If you are running it on heating P8 error will appear because the disc pressure is too high. It could be overcharged.
Posted on Jun 01, 2009
CH02- Means "Indoor coil sensor is faulty or not connected"
Posted on Nov 19, 2009
Testimonial: "thanks for help i will keep you posted when ever I have a problem"
continuous flash is frost prevention ...clean the filter & switch fan to high
flashes once every 2 sec could be room air sensor contact loose/short...call dealer
flashes 2x every 2 sec is indoor coil sensor contact loose/short...call dealer
flashes 3x / 2sec sensor contact problem, or compressor overload protection trip or gas leak...call dealer
Posted on Jun 02, 2010
Tips for a great answer:
May 29, 2016 | Mitsubishi Heating & Cooling
Dec 28, 2010 | Electrolux Heating & Cooling
Dec 11, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Nov 19, 2009 | Heating & Cooling
Nov 24, 2008 | Panasonic CW-C60RU Air Conditioner
May 24, 2017 | Refrigerators
55 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: