Question about Goodman CKL42AR42 Air Conditioner
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
Sounds like you have a bad capacitor for your squirrel cage fan , now as for the a/c unit sounds like you have a direct short in compressor to ground or leg to leg , check all wiring to make sure that it is not grounding out or melted together.
Posted on Jul 23, 2009
SOURCE: Inside fan running outside not
There is an electrical box on the wall near the outdoor unit. open it and be sure that the circuit breaker is in the on position. Same in your electrical panel, be sure that the circuit breaker is turned on.
Posted on Aug 16, 2009
You're unit is a 31/2 ton according to the numbers.Normally, breakers will only be in a half way posistion when tripped. Yes, under most conditions, the fuse will blow before the breaker trips. I have seen this many times, the breaker may be weak, burned, loose wires and so tighten wires, check the condition of the breaker.It sounds like the breaker even though it is 60 amps, is the problem and you should replace it with out hesitating. This will solve you're problem. When you pull the breaker out, look at the metal clips that snap in on the buss bar to see if they have been overheating.And the buss bar its self. You will know. I am sure this will take care of you're problem. Good Luck,
Posted on Dec 07, 2009
Testimonial: "Thank a lot this was very helpful"
This means that the condenser fan motor (outside unit) failed, this caused to build hi pressure and either activated a safety valve to release the extra pressure or blew a line and R22 Refrigerant escaped from system.
The fix is to replace motor fan and capacitor find the leak and refill system with R22 Refrigerant Gas. It is safe to turn on the Fan Only mode on the Thermostat until a HVAC Tech arrives.
To perform this job parts and labor included will cost: about $300 -.$400. Look on the Yellow Pages for a Tech in your neighborhood.
Good Luck!! Don't forget to Rate this post!!
Posted on Aug 13, 2010
Tips for a great answer:
Dec 11, 2014 | Ruud UBHC Air Conditioner
Feb 07, 2014 | Goodman CKL60AR60 Air Conditioner
Jan 06, 2014 | Electrical Supplies
Jun 06, 2010 | Dometic Rooftop RV Air Conditioner
Aug 17, 2009 | Ruud Matching Split Air Conditioner
Jul 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jul 06, 2009 | Dometic Rooftop RV Air Conditioner
Nov 05, 2008 | Dometic Rooftop RV Air Conditioner
Jun 08, 2008 | Goodman CLQ36AR49 Air Conditioner
Sep 03, 2007 | Heating & Cooling
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: