Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like your condenser fan motor may be locked up or the capacitor that helps give the condenser fan motor a kick to get it started may be defective. Try turning your system on and using a long screwdriver try to push the fan blade on the condenser fan motor to see if it will run normally if you give it the starting boost it needs.If it does run at full speed and doesn't over heat or start and then slow down then you probably only need to replace a simple 10-12$ capacitor. If it barely turns, makes an odd humming sound or overheats etc. then you will have to replace the condenser fan motor. This is assuming that the outdoor condenser has the 220v supplied and the 24v supplied to the compressor relay, that the compressor relay is engaged and suppling 220v to the condenser fan motor.
Posted on May 30, 2008
you must have very old equipment are you sure of the model and serial number it might be a 69 if the serial number is the m0696. Tom double check those numbers.
Posted on Jun 28, 2009
1) you probably have a clogged drain line and
2) your air handler coil may be dirt.
1) Using a dry/wet vacuum cleaner, attach it to the drain line outside and **** all the gunk out of a drain line; or using a water hose, attach it to from inside right by the air handler and push the gunk out with the force of water - be careful using this method. Or simply pour draino into the air handler pan, wait for 10 minutes and using a cup pour water in the pan to see if it drains fine.
2) if the coil is dirt and it ices up, call a technician to for coil cleaning.
Posted on Oct 12, 2009
Tips for a great answer:
Jul 25, 2015 | Ruud Heating & Cooling
May 18, 2011 | Ruud Matching Split Air Conditioner
Jan 07, 2011 | Heating & Cooling
Jul 20, 2010 | Ruud Heating & Cooling
Jun 16, 2010 | Ruud UBHC Air Conditioner
Nov 03, 2009 | Ruud UBHC Air Conditioner
Aug 06, 2009 | Heating & Cooling
May 23, 2018 | Coleman Heating & Cooling
36 people viewed this question
Usually answered in minutes!