Question about Heating & Cooling
Compressor on air conditioner runs for 5 seconds then cuts out,after a few minutes cuts back in, runs for 5 seconds and then turns off airconditioner.after minute or two cuts back in compressor runs 5 seconds cuts out and so on
-If both compressor and fan motor starts and stop, thermostat is the defect.
- If only the compressor check for your outlet no sign of discoloration, check the voltage if normal, check the defective overload protector of the compressor it its external, or compressor itself is defective
Posted on Jan 04, 2008
Your unit will be low on refrigerant gas. When the A/C unit starts, the suction side of the system pulls the pressure down below the safety cut out pressure and stops the compressor. after a few seconds of compressor not running and therefor not lowering the pressure on the suction side of the system, the pressure will rise again till the safety cutout resets, and it starts all over again. Repair leak, regas system and it should work fine.
Posted on Apr 27, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2017 | Heating & Cooling
Sep 10, 2015 | Hitachi Heating & Cooling
Apr 27, 2014 | Haier Amana Apn14j-E Portable Air...
Dec 06, 2013 | Mitsubishi Montero Sport Cars & Trucks
Aug 30, 2010 | Whirlpool ACC184PS Thru-Wall/Window Air...
Jun 20, 2010 | Haier ESA3085 Thru-Wall/Window Air...
Jun 07, 2010 | Samsung AW1203B Air Conditioner
Jun 23, 2009 | Dometic Rooftop RV Air Conditioner
Feb 01, 2009 | Heating & Cooling
2,369 people viewed this question
Usually answered in minutes!