Question about Ruud UBHC Air Conditioner
Outside compressor unit not blowing. The solenoid is engaged and have tried cleaing the contact points with flat screwdriver and compressed air.
If fan is not on check to make sure gettion 230 v to unit the contactor is 24v controled by the indoor unit look at the capacitor to make sure not swelled up on top if so bad you can turn off power and jump around contactor if you feel it is pitted to bad to run unit most of time when bad they weld together a new one is adout 15.0 seperate wires with zip ties to not get mixed up also check wires at compressor they sometimes come off hopr this helps
Posted on Jun 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 12, 2014 | Fujitsu Heating & Cooling
Jun 25, 2014 | Dometic Rooftop RV Air Conditioner
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Jul 01, 2011 | 2002 Dodge Neon
Jun 30, 2011 | 2001 Dodge Ram 1500 Truck 2WD
Sep 03, 2010 | Goodman CKL42AR42 Air Conditioner
Jul 09, 2010 | Carrier 38CKC048 Air Conditioner
Jul 08, 2010 | Frigidaire FAA065M7A Air Conditioner
Jul 04, 2008 | Heating & Cooling
138 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: