Question about Heating & Cooling
The problems cold be to small a return air. I do a lot of cool surveys where I check the efficiency of the AC. Some people are putting in Heppa pleated filters and they realy restrict the air flow a great deal. You need at least 1.25 square feet of filter area per ton. 5 ton should have 24 by 36 return. Check to see if coil is dirty. Check air temp. across coil. From return to closest vent. Should be between 18 to 23 degress. Rusty
Posted on Jun 03, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 23, 2015 | Norpole 5000BTU Mechanical Window Air...
Jun 14, 2014 | Rheem 13AJA30A01 2.5 Ton 13 SEER R22 Air...
Jun 05, 2014 | Gibson JS5BD042KA 3.5Ton 13 Seer R22...
Jul 18, 2012 | Goodman Heating & Cooling
Aug 17, 2010 | Intertherm P3RA-048K Air Conditioner
Aug 29, 2009 | Heating & Cooling
May 14, 2009 | Heating & Cooling
May 06, 2009 | Goodman Heating & Cooling
Jul 29, 2008 | Goodman CKL60AR60 Air Conditioner
181 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: