Question about Heating & Cooling
Goodman CK36-18: Outside fan kicks on, but compressor does not run. There are two control/signal wires coming from the house. I made sure those connections were good. I here an occassional noise, as though the capacitor is trying to start the compressor. The noise is there briefly, and then goes away.
Sounds like a bad capacitor. They can be bad and the fan will still run. Turn off power and check for burnt wires on the top of the contactor going to the capacitor or on the top of the capacitor.. Check terminals on the compressor also. When capacitors go bad they are slightly swollen. They can also look good and be bad . Could be compressor but start with capacitir and wires. IWork on a lot goodman units. Most of the time it is the cap.
Posted on Jun 03, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 29, 2016 | Goodman Heating & Cooling
Jun 14, 2012 | Goodman Heating & Cooling
Sep 11, 2011 | Goodman CKL36AR36 Air Conditioner
Jul 20, 2009 | Goodman CKL42AR42 Air Conditioner
Jun 23, 2009 | Goodman CKL30AR30 Air Conditioner
Jun 11, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 06, 2009 | Goodman CKL42AR42 Air Conditioner
811 people viewed this question
Usually answered in minutes!