Question about Dynex (TE685AVR) UPS System
I have owned a Dynex surge protector (model Te685avr) for almost 6 years now. Two days ago I was out of the house and we lost power for an hour. When I came back my computer had shut down. What I assumed happened is that while I was gone my backup power on the Dynex surge protector ran out. The problem I have now is the 3 outlets on the side that are powered by "backup power" don't work. I have unplugged all the cords going into the unit for a whole day to charge the unit but I still cant get the outlets on the "backup" side of the surge protector to work. The 3 outlets on the otherside work just fine, but they are not backed up with power. Any suggestions to get the other 3 to work, they have no power running to them? I have a Dynex 800 u UPS and the battery side of the device has no power but the surge side does. I think the battery inside of the unit needs to be replaced but have no idea where I would find one because Dynex no longer supports this unit. Any help would be great.
The sealed batteries in these last about 6 years. You are correct in thinking that you may need a new one. Very easy to install. Here's a supplier of these: http://www.batteryinternational.com/dynex-te685avr-ups-battery-ups-batteries-f1.html
Posted on Jun 02, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 08, 2011 | APC BE325 SURGE PROTECTOR + BATTERY...
Oct 21, 2009 | Dynex (TE685AVR) UPS System
Nov 09, 2008 | Dynex (TE685AVR) UPS System
Jun 26, 2008 | Dynex (TE685AVR) UPS System
Jan 10, 2008 | Dynex (TE685AVR) UPS System
Nov 18, 2007 | Cybernet Systems CyberPower 625AVR...
May 08, 2017 | Dynex (TE685AVR) UPS System
296 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: