Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
When I set the thermostat on my home air conditioner to "Fan On" (rather than auto), the compressor engages no matter what the temperature setting. In other words, it doesn't merely recirculate the air but continues cooling.
Sounds like you have a wire shorted between y and g somewhere. Maybe a bad tstat. email me if you have more problems firstname.lastname@example.org and I may be able to walk you thru the troubleshooting
Posted on Jun 04, 2009
You could have some wires touching or a bad t stat. take the cover off t stat after cutting power to furnace either at the furnace or breaker box. take wires off terminals G and R on t stat and wire nut them together return power. the fan should only be running. it compressor comes on with is cut power to furnace un hook all the wires make sure they aren't touching leave R and G together see if compressor comes on if so do the same thing on furnace with a jumper accross R and G. if the compresor comes on again un hook all the stat wires on furnace and t stat and ohm the wires out to see if you have resistance between any of the two wires together. if you do you have a short if the fan comes on by it's self any time while hooking wires on R and G together you have a bad t stat
Posted on Aug 08, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 30, 2016 | Heating & Cooling
on Sep 21, 2010 | Heating & Cooling
Jul 21, 2015 | Dometic Rooftop RV Air Conditioner
Mar 21, 2015 | Dometic Rooftop RV Air Conditioner
Oct 30, 2012 | Heating & Cooling
Nov 16, 2010 | Weather King 10AJA6001AH Air Conditioner
Jun 04, 2008 | Coleman Mach III Air Conditioner
238 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: