Question about Weather King 10AJA2501AH Air Conditioner
My exterior one year old Weather King fan keeps blowing one of the fuses. Please help. When the air conditioner kicks on it blows a fuse in the furnace near the blower (looks like a 10amp car fuse connected to 2 wires). I replaced the fuse, turned the power back on, and it immediately blew the fuse but didn't kick on. The fan, heat, or cool will not work. What could be causing that little fuse to blow over and over again? It was working fine 2 days ago!
You probably have a shorted wire between the heater and the a/c. There are two wires that conncet the control power to the outdoor a/c from the heater they should be on terminal c & y in the heater. disconect those two wires and try it again if the fuse doesnt blow you have a short in the wire between the a/c & heater
Posted on Jun 03, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 25, 2013 | Weather King Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 11, 2011 | Heating & Cooling
Dec 12, 2010 | Heating & Cooling
Jun 14, 2010 | Weather King 10AJA3001AH Air Conditioner
Jan 13, 2009 | Weather King 12AJA4801AH Air Conditioner
Dec 29, 2008 | Weather King 12AJA4801AH Air Conditioner
Dec 17, 2008 | Weather King 10AJA3601AH Air Conditioner
Aug 30, 2008 | Weather King 10AJA2501AH Air Conditioner
Aug 08, 2008 | Weather King 12AJA6001AH Air Conditioner
279 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: