Question about GE Heating & Cooling
2 brown wires go to a split capacitor if you have a dual cap which has three terminals marked comp fan com if u have this type of capacitor then the brown wire goes to fan and the brown and white gets capped with a wire nut. whenever replacing a fan motor you should also replace the cap or at least check the capacitance to see if it is still good. you have to check it with a meter that test microfarad.you can get a permanent split capacitor and mount it in there then u use the brown on one side and the brown and white on the other side it only has 2 terminals.
Posted on May 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 24, 2014 | Heating & Cooling
Mar 02, 2014 | Computers & Internet
Oct 03, 2012 | Heating & Cooling
Apr 10, 2017 | Heating & Cooling
Jul 25, 2011 | Heating & Cooling
Jul 09, 2010 | Heating & Cooling
Jun 09, 2010 | Heating & Cooling
Apr 27, 2009 | Heating & Cooling
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
Apr 28, 2017 | GE Heating & Cooling
191 people viewed this question
Usually answered in minutes!